Learn about the supported feature codes that are available for T00, T42 and racks. T00, T42 or racks can be bolted together in a multiple rack arrangement. This figure shows that arrangement. Racks can be heavy when populated with several drawers. Use the Weight distribution distances for racks when loaded and Floor loading for.
|Published (Last):||2 January 2006|
|PDF File Size:||5.59 Mb|
|ePub File Size:||15.71 Mb|
|Price:||Free* [*Free Regsitration Required]|
As an example, feature code 70114-t00 approximately 45 kg lbs so the new Maximum Weight of Drawers the rack can support in a zone 4 earthquake environment is kg lbs.
No Rack Content Specify: Both Side Panel For 1. This equates to The appropriate DC power cables are included with the supported drawer systems and plug into the power connectors at the rear of the PDP.
This unit is the same as the base unit Two or more Junction Boxes Minimum required: A maximum of twelve drawers can be installed in a rack that has a single or PDU.
Power source loading maximum in kVA 2. Racks ordered with volts DC power are available in black.
T00, T00, and racks multiple attachment
Front and rear acoustic doors for 1. The T00 does not include feature codes for ordering circuit breakers. The front end of the PDU will be firmly attached to the rear of the rack. Up to 2 additional PDUs can be installed horizontally in the rear of the rack, in the space that is normally used for rack-mounted drawers.
A 1U blank panel for the front of the rack for air-flow control is included. It allows heavier equipment to be handled more safely by fewer people. No max OS level required: The following table shows the necessary floor loading for the T00T42 and racks when loaded.
The trim pieces cover the space between each rack for an enhanced appearance and for additional protection of the equipment inside the racks. For comparison, this is most similar to the earlier generation PDU, but offers C13 receptacles Limitation: Reserves rack space Attributes required: This PDU requires 3-phase electrical service.
No Ruggedized Rack Feature For enhanced rigidity and stability of the rack, the optional Ruggedized Rack Feature provides additional hardware that reinforces the rack and anchors it to the floor. Some products can have rack installation limitations. Appropriate power cables and circuit breakers are included, which will vary depending on the types and quantities of CPU systems and storage subsystems to be installed in the rack.
The feature includes a large steel brace or truss that bolts into the rear ibbm the rack. For OEM equipment the customer must provide an applicable DC power cable and associated pluggable circuit breaker.
IBM 7014-t00 36u Server Cabinet
7014t00 acoustic doors, front and rear. Machine Type Rack order Minimum required: Models and MMA are not compatible with the trim kit. Next 2 will be mounted horizontally in the rear of the rack, and will occupy 1U of 7014-g00 space for each PDU. No Max OS level required: Including rectify the PDU, power supplies, and line cords? This equipment is subject to FCC rules; it will comply with the appropriate FCC rules before final delivery to the buyer or center of distribution. Please sign in to contact the vendor E-mail.
Maximum weight of fully populated rack, units are lb with kg in parentheses. Side panels are needed only for the two end racks of the suite.
Optional 70144-t00 rack feature provides added earthquake protection with modular rear brace, concrete floor bolt down hardware, and bolt-in steel front filler panels. If is not on the initial rack order, component placement within the rack will be determined by IBM. Model T42, B42, and rack.